An alternate system uses a fog or great mist injected in to the intake air stream. Although a number of commercial systems can be found, growers can assemble and install their own system utilizing a high pressure piston pump and fog nozzles. The basic components are proven in Fig. 1. A two-stage system controlled by a two- stage thermostat enables more water to be applied on excessively warm, bright days. Temperature settings ought to be 5-10°F apart.
Algae development in the pads may become a problem which will decrease the effectiveness of the system and lead to accelerated deterioration of the pads. The addition of an algaecide to the drinking water supply can help in control.
It is desirable, especially in hard drinking water areas, to add a wetting agent to the drinking water to obtain additional uniform wetting of the pads. A commercial material or liquid household detergent at the rate of 2 tablespoons per 100 gallons may be used.
Water for the pads should be clean and low in mineral content to prevent clogging and coating of the pads. A pump, pipes and gutters are accustomed to recirculate the drinking water. A flow rate 113 gallon each and every minute per linear foot of pad system ought to be provided to assure adequate wetting.
In the most typical coolant system (fan and pad), the fans draw air through wet pads that prolong the length of one endwall or sidewall. Aspen and coated cellulose are common pad materials that usually have life of 1 to three years. Approximately one sq . foot of pad are is necessary for 20 square feet of floor area.
If you would certainly like even more info on Greenhouse Exhaust Fan, please do not hesitate to call us.